The starting mode and testing method of Water pump？ Wroten by TDRFORCE Water Pump Factory or Manufacturer
Published on https://tdrpump.com
About the Publisher: TDRFORCE Factory or Manufacturer direct Online Sale Drinking Water Pump, RV Water Pump, Pressure Booster Pump, Sump Pump, Hot Water Pump,Submersible Pump, Liquid Transfer Pump, Garden Pump, Irrigation Pump, Pond Pump, Customized Pump etc
Description:The starting mode and testing method of Water pump？ Let's follow the guide from TDRFORCE Pump Factory or Manufacturer.
The starting mode and testing method of Water pump？The Pump Tech From TDRFORCE Water Pump Factroy|Manufacturer?
First, the Water pump start mode includes automatic start and manual start two ways
- Automatic start mode: when a require occurs, the water controller can directly automatically start the fire pump after receiving the pressure switch signal of the alarm valve group, or directly start the water pump after receiving the low-pressure pressure switch of the system pipe network pressure;It can also accept automatic water alarm controller to control the linkage signal to start the water pump.
- Manual start mode: a manual button is set on the linkage control cabinet in the fire control room to directly start and stop any water pump, and a manual button is set on the control cabinet of Water pump to directly start and stop any fire pump.
Water pump detection method (Water pump operation method)
(1) Prepare before opening the pump
- Check whether the pump and system parts are complete and intact.For example, whether all fasteners are fastened;Whether the coupling clearance is appropriate;Whether the oil injection hole of the water pump has been filled with oil according to the provisions;Whether the instrument valve is in good condition.
2, the manual car is normal, should not be heavy, otherwise should find out the reason for processing.
- When checking the mechanical part, the pump circuit switch shall not be closed so that the motor is in a live state, and the sign "Operated by someone, not allowed to close" shall be hung on the distribution cabinet.
4, check whether the system pressure is normal, if not normal, should find out the cause of the system to deal with.
- Check whether there are bubbles, bubbles, drops and leaks in the system, and deal with them in time if any.(The normal dripping of the pump shaft is not included, and the water drop shall not exceed 1 drop per second)
(2) Operation process
- Open the inlet valve and outlet valve.
- Switch the water pump control cabinet to the "manual" state.
- Press the "Start" button to start the water supply of the pump, and press the "Stop" button to stop the water supply after checking that there is no problem.
- Turn the upper transfer switch of the control cabinet to the "automatic" position, and the water pump will enter the running state of self-feeding.